Slam Sut-off valve is installed immediately after the filter & prior to the Regulator. It normally remains open, incase the outlet pressure of the regulator exceeds the permissible limits, the slam shut off valve senses it through the impulse line & immediately shuts off the flow to downstream.When theregulatorisrepaired,theslamshutoffvalveistobeopenmanuallybypullingtheknob.Oncetheflowstartsthroughthe slam shut off valve it will remain open till the outlet pressure of the regulator is within limits.
Working Pressure 250 Bar
Flow Rate 500 Nm3/hr
Shut Off Pressure Setting 20 to 100 kg/cm²
End Connection 1 BSPF on both side.
Medium CNG,Nitrogen, Carbon dioxide, Air
Available in Self sensing & External sensing.