Slam Sut-off valve is installed immediately after the filter & prior to the Regulator. It normally remains open, incase the outlet pressure of the regulator exceeds the permissible limits, the slam shut off valve senses it through the impulse line & immediately shuts off the flow to downstream.When theregulatorisrepaired,theslamshutoffvalveistobeopenmanuallybypullingtheknob.Oncetheflowstartsthroughthe slam shut off valve it will remain open till the outlet pressure of the regulator is within limits.
Working Pressure 20 kg/cm²
Flow Rate 500 Nm3/hr
Shut Off Pressure Setting 0.05 – 5 bar
End Connection 4322 11?2 BSPF, 4327 11?2 Flanged, 4328 2″ Flanged, 4329 3″ Flanged, 4330 4″ Flanged, 4332 2″ BSPF
Medium LPG, Natural Gas, Oxygen, Nitrogen, Carbon dioxide, Air
Available in External sensing.
Will be supplied for assembly in gas train only.